When installing repairing or replacing efficient gas furnace, it is very important to properly plan the layout of the vent and the combustion air piping. The installer must route the flue and combustion air pipes in the most direct route as possible. Also, be sure that you use the minimum amount of elbows, 45s, and other fittings when you begin to construct the piping.
It is highly recommended that all furnaces have a two-pipe configuration. All vents must terminate in the same atmospheric zone. The vent can be vented horizontally, vertically through the roof, or outside of the house.
Horizontal vent runs slightly sloped upwards from the furnace one quarter inch for every horizontal running foot of vent and should be supported every five feet of linear vent length. This will ensure that any water or condensation that forms inside the flue pipe will drain properly back towards the furnace.
When selecting the size of the vent pipe, follow the vent piping chart. A good rule to follow is any furnace over 80,000 BTUs and above should run in 3 inch PVC. If you follow this rule, you will eliminate nuisance trips to the pressure switch and limit switch trips.
We are available 24/7 any time to serve you with any Gas Furnace Installation, repair and maintenance, feel free to contact us at any time.
Find out more about furnace repair:
One of the most common reasons for heating repair service in New Jersey is a gas furnace that
If you re like most people in Chester Township your furnace gets heavy use during the fall and winter
New Jersey Heating Company Providing Furnace repair Installation Service 24 7 in Bergen County Morris county Union County
One of the easiest and really one of first and most important steps that you may consider when
Fix Your Home Furnace Or Heater - Repair Help and Maintenance It s that time of the year and
hvac repair services in nj 24- hour same day heating repair and ac system repair around me by